These guide specifications are provided for the Professional to insert into their Technical Specifications. These shall be edited using the process described in the instructions contained at the beginning of the document. Use of other BAS specifications is not acceptable.
Any specification section (Mechanical or Electrical) that specifies a sub-system to be integrated with the University's Building Automation System (BAS) shall include specification-text that refers to Figure 1 and Figure 2 at the end of the Building Automation System specification (15900). This document addresses this requirement.
BACnet Instance, IP and Network Numbering (see description)
Process to be used to obtain BACnet and Network Numbers for construction jobs.
This document contains design considerations and selection criteria to achieve uniform selection and installations if using pressure independent control valves. This is not intended to require PIC valves in all cases.
Standard Microblock Names are to be used in the Programming. Current naming conventions were developed specific to ALC Programs that exist with Standard Sequences of Operation. Consistency will improve troubleshooting.